Four major manifestations of fluorine deficiency in industrial chillers
After using the industrial chiller for a period of time, due to insufficient fluorine, it is necessary to check whether fluorine should be added at this time. For chillers, what are the specific manifestations of fluoride deficiency? Today, Anyda will share with you the four major manifestations of fluorine deficiency in industrial chillers.
1. Compressor load increases
There are many reasons for the increased compressor load. However, if the industrial chiller lacks fluorine, the compressor load will inevitably increase. If the air-cooled and water-cooled systems do not have poor heat dissipation, the compressor load is often caused by insufficient fluorine.
2. The cooling capacity decreases and the cooling efficiency decreases
When the refrigeration capacity of industrial chillers decreases, there may be many reasons, but the chiller lacks fluorine, especially when there is a large amount of fluorine deficiency, the refrigeration capacity of the chiller will definitely drop significantly, which will definitely affect the production efficiency of the enterprise.
3, high exhaust temperature
High exhaust temperature is a common phenomenon in industrial chillers. The pressure and thermometer at the exhaust end can clearly read the exhaust temperature. High exhaust temperature is not an uncommon phenomenon. Many people face the high exhaust temperature of chillers. Negative response, in fact, high exhaust temperature is caused by abnormal operation of the oil separator and insufficient refrigerating lubricant
4, high energy consumption, large compressor wear
Insufficient refrigerant, industrial chillers cannot meet the refrigeration demand, the chilled water outlet temperature does not meet the standard, the compressor will increase the load to meet the chilled water outlet demand, power resources are consumed, and the compressor wears out.
That is to say, in many cases, it is not easy to observe fluorine deficiency, especially for large industrial industrial chillers. If the refrigeration capacity and refrigeration efficiency decrease slightly, it is difficult to find it immediately. It is recommended to the staff of the chiller manufacturer It can be detected with an electronic detector. The high probability of fluorine deficiency is due to problems in refrigerant management and refrigerant flow pipes such as condensers, valves, etc. In the case of fluorine deficiency, it is necessary to detect leakage, determine the location of the leakage, and then collect , After confirming that the refrigerant does not leak, and after the collection is unsuccessful, start the refrigerator operation.