High Performance Air Cooled Water Chiller
1. Easy to install and clean
2. Save time and have high effciency
3. With installed automatic watering device
4. Excellent throtting technology
5. Rustproof, anti-vibration, low noise and safe
Shen Zhen Anyda Refrigeration Machinery Co., Ltd. is a high-tech private enterprise which was established in 2004 and is specialized in the research, production and trading of industrial refrigeration technology and facilities. We have gradually produced Industrial Chiller,Water Chiller,Air Cooler,Oil Chiller,Low Temperature Chillers,Hot Water Chiller, Heat Pumps and Central Air Conditioner which are widely applied to plastic & rubber machinery, daily-use chemical, textile, general machinery, laser machinery, LCD and PCB industry, electroplating, equipments of laboratory, food, pharmacy, etc . Now we own more than one hundred staff and about twenty of them are engineers with high grade titles. We gained the certification of ISO9001:2008 and CE international quality management systems. We are looking forward to your suggestion, and are confident of becoming your choice !
1.How does a chiller system work?
Chiller has two circulation,one is process water circulation,the other is refrigerant gas circulation.Heat picked up from the process.Heat transfers to refrigerant circulation.Heat is remove to air or water.
2.How to calculate cooling capacity for chillers?
Cooling Capacity(kw)= Flow Rate(m3/h)*Temp Change(T1-t2)/0.86
Heat Load= C(specific heat)* M(quality output per hour )*Temp Change(T1-T2)
3.Types of chiller system?
Air Cooled Chiller and Water Cooled Chiller.Water cooled chiller needs a separated cooling tower and has a higher efficiency,but less easier than air cooled.
4.Cooling capacity unit conversion?
1 kcal/h = 1.163W,1 W = 0.8598 kcal/h;
1 Btu/h = 0.2931W,1 W = 3.412 Btu/h;
1 USRT = 3.517 kW,1 kW = 0.28434 USRT;
1 kcal/h = 3.968 Btu/h,1 Btu/h = 0.252 kcal/h;
1 USRT = 3024 kcal/h,10000 kcal/h = 3.3069 USRT;
5.The chiller can heat?
Yes,by the electrical heating wire.Please kindly inform us the hot water temp or heating capacity.
Step 1: Keep Tubes Clean
Step 2: Ensure a Leak-free Unit
Step 3: Sustain Proper Water Treatment(prevent scale, corrosion)
Step 4: Analyze Oil and Refrigerant
7. Contact information?
Tel: (755) 84074988, 89260299
Add: NO.6-2 west of egongling industrial district,pingdi street,longgang district,China