Packaged 30 Ton 40 HP 110 Kw Air Cooling Water Chiller With Copeland Compressor Description:
1.Anyda electrical air cooled chiller use high efficiency semi-hermetic screw compressor
It can realize 4 steps or stepless capacity control. The unique squirrel cage compressor motor started up by Y type can decrease start current by 33%, automatically cooled by the refrigerant.
2.Anyda electrical air cooled chiller use high efficiency air side heat exchanger
Unique M-shaped design, inner grooved & patent sawtooth design and hydrophilic aluminum fin guarantee efficient heat exchange between the air side exchanger and ambient air.
3.Anyda electrical air cooled chiller use shell & tube heat exchanger
Dry type & tube heat exchanger with inner grooved copper tube optimizes the cooling & heating efficiency. Self-cleaning, high intensity, anti-shaking design and heat insulation covering material ensure shell & tube heat exchanger unstained, reliable, quiet, highly efficient.
4.Anyda electrical air cooled chiller equipped with complete protection
Water shortage protection, high/low voltage protection, anti-freezing protection, overload protection, overheat protection and oil level protection ensure high reliability and stability.
Applied Machinery: Cooling system of oil temperature, ultrasonic, high frequency machinery,injection molding machinery, blow molding machinery.
|Item||Specification / Supplier|
|Temp Outlet (ºC)||5-35|
|refrigerant control||Expansion valve|
|Evaporator||Style||Shell and Tube / 1set|
|Cold water flow(m3/h)||19|
2.Fan overload protector
3.High/low voltage protector
|Electronic||LS / Carlo|
1.How does a chiller system work?
Chiller has two circulation,one is process water circulation,the other is refrigerant gas circulation.Heat picked up from the process.Heat transfers to refrigerant circulation.Heat is remove to air or water.
2.How to calculate cooling capacity for chillers
Cooling Capacity(kw)= Flow Rate(m3/h)*Temp Change(T1-t2)/0.86
Heat Load= C(specific heat)* M(quality output per hour )*Temp Change(T1-T2)
3.Types of chiller system?
Air Cooled Chiller and Water Cooled Chiller.Water cooled chiller needs a separated cooling tower and has a higher efficiency,but less easier than air cooled.
4.Cooling capacity unit conversion?
1 kcal/h = 1.163W,1 W = 0.8598 kcal/h;
1 Btu/h = 0.2931W,1 W = 3.412 Btu/h;
1 USRT = 3.517 kW,1 kW = 0.28434 USRT;
1 kcal/h = 3.968 Btu/h,1 Btu/h = 0.252 kcal/h;
1 USRT = 3024 kcal/h,10000 kcal/h = 3.3069 USRT;
5.This chiller could do heat recovery?
Yes,please kindly send us the temp and water volume per hour.
Step 1: Keep Tubes Clean
Step 2: Ensure a Leak-free Unit
Step 3: Sustain Proper Water Treatment(prevent scale, corrosion)
Step 4: Analyze Oil and Refrigerant
Why Choose Us?
1.Reply your inquiry within 12 working hrs.
2.Strong R&D team,more than 15 years of manufacturing chiller experience. OEM&ODM is welcomed.
3.Direct factory,offer customer competitive price with high quality chiller.
4.Strict quality control system,professional QC team.